[R.O. 2012 § 705.005; Ord. No. 287, 4-20-2004]
This Chapter identifies Kimberling City's requirements for the use of public sewers and the description of the types of wastes permitted to be discharged into the public sewers. It also identifies the construction and use of private sewage disposal systems when a public sewer is not available.
[R.O. 2012 § 705.010; Ord. No. 287, 4-20-2004; Ord. No. 340, 10-6-2009]
Chapter 500, Building Codes, Section 500.010, Adoption of the 2006 International Building Code; Section 500.050, Adoption of the 2006 International Plumbing Code; and Section 500.110, Adoption of the 2006 International Property Maintenance Code shall apply to this Chapter to the extent referenced herein, except that the use of metal septic tanks shall be prohibited in the City of Kimberling City.
[R.O. 2012 § 705.015; Ord. No. 287, 4-20-2004; Ord. No. 340, 10-6-2009]
Unless the context specifically indicates otherwise, the meaning of the terms used in this Chapter shall be as follows:
- BOD (denoting BIOCHEMICAL OXYGEN DEMAND)
- The quantity of oxygen utilized in the biochemical oxidation of organic matter under standard laboratory procedure in five (5) days at twenty degrees Celsius (20° C.), expressed in milligrams per liter.
- BUILDING SEWER
- That part of the lowest horizontal piping of a drainage system which carries waste and conveys it to the City sewer. The extension from the building sewer to the public sewer or other place of disposal.
- Solid wastes from the domestic and commercial preparation, cooking and dispensing of food and from the handling, storage and sale of produce.
- INDUSTRIAL WASTES
- The liquid wastes from industrial manufacturing processes, trade or business as distinct from sanitary sewage.
- INFLOW AND INFILTRATION (I&I)
- Inflow and Infiltration (I&I) is defined by the U.S. Environmental Protection Agency (EPA) as: "Infiltration is the seepage of ground water into the pipes or manholes through defects such as cracks, broken joints, etc. Inflow is the water which enters the sewer through direct connections such as roof leaders, from storm drains or yard, area and foundation drains. . ."
- NATURAL OUTLET
- Any outlet into a watercourse, pond, ditch, lake or other body of surface or ground water.
- Any individual, firm, company, association, society, corporation or group.
- The logarithm of the reciprocal of the weight of hydrogen ions in moles per liter of solution.
- PROPERLY SHREDDED GARBAGE
- The wastes from the preparation, cooking and dispensing of food that have been shredded to such a degree that all particles will be carried freely under the flow conditions normally prevailing in public sewers with no particle greater than one-half (1/2) inch (one and twenty-seven tenths (1.27) centimeters) in any dimension.
- PUBLIC SEWER
- A sewer in which all property owners of abutting properties have equal rights and is controlled by public authority. This includes all appurtenances.
- SANITARY SEWER
- A sewer which carries sewage and which storm, surface and ground waters are not admitted.
- A combination of the water-carried wastes from residences, business buildings, institutions and industrial establishments.
- SEWAGE TREATMENT PLANT
- Any arrangement of devices and structures used for treating sewage.
- SEWAGE WORKS
- All means of collecting, pumping, treating and disposing of sewage. Any devices and systems for the storage, treatment, recycling and reclamation of municipal sewage, domestic sewage or liquid industrial wastes. These include intercepting sewers, outfall sewers, sewage collection systems, individual systems, pumping, power and other equipment and their appurtenances; extensions, improvements, remodeling, additions and alterations thereof; elements essential to provide a reliable recycled supply such as standby treatment units and clean well facilities; and any works, including site acquisition of the land, that will be an integral part of the treatment process or is used for ultimate disposal of residues resulting from such treatment; or any other method or system for preventing, abating, reducing, storing, treating, separating or disposing of municipal waste or industrial waste.
- SEWAGE DISPOSAL SYSTEM
- Any device or combination of devices, piping or storage structure for treating and/or holding sewage.
- SEWER LINE
- A pipe for carrying sewage.
- Is mandatory; MAY: Is permissive.
- Any discharge of water, sewage or industrial waste which in concentration of any given constituent or in quantity of flow exceeds for any period of duration longer than fifteen (15) minutes more than five (5) times the average twenty-four-hour concentration or flows during normal operation.
- STORM DRAIN SYSTEM
- A system which carries storm and surface waters for drainage purposes. Any device or combination of devices, piping or structure for carrying or holding said water.
- SUSPENDED SOLIDS
- Solids that either float on the surface of or are in suspension in water, sewage or other liquids and which are removable by laboratory filtering.
- TREATMENT WORKS
- Any devices and systems for the storage, treatment, recycling and reclamation of municipal sewage, domestic sewage or liquid industrial wastes. These include intercepting sewers, outfall sewers, sewage collection systems, individual systems, pumping, power and other equipment and their appurtenances; extensions, improvements, remodeling, additions and alterations thereof; elements essential to provide a reliable recycled supply such as standby treatment units and clean well facilities; and any works, including site acquisition of the land, that will be an integral part of the treatment process or is used for ultimate disposal of residues resulting from such treatment; or any other method or system for preventing, abating, reducing, storing, treating, separating or disposing of municipal waste or industrial waste.
- A channel in which a flow of water occurs, either continuously or intermittently.
[R.O. 2012 § 705.020; Ord. No. 287, 4-20-2004]
It shall be unlawful for any person to place, deposit or permit to be deposited in any unsanitary manner on public or private property within the City of Kimberling City, or in any area under the jurisdiction of said City, any human or animal excrement, garbage or other objectionable waste.
It shall be unlawful to discharge to any natural outlet within the City of Kimberling City, or in any area under the jurisdiction of said City, any sewage or other polluted waters, except for DNR-approved City owned and operated sewage treatment plants.
Except as hereinafter provided, it shall be unlawful to construct or maintain any privy, privy vault, septic tank, cesspool or other facility intended or used for the disposal of sewage.
The owner of all houses, buildings or properties used for human habitation, employment, recreation or other purposes situated within the City of Kimberling City shall install suitable toilet facilities therein and shall connect such facilities directly with the public sewer in accordance with the provisions of this Chapter within sixty (60) days after the date of official notice to do so, provided that the public sewer is available within three hundred (300) feet of the property line.
[R.O. 2012 § 705.030; Ord. No. 287, 4-20-2004]
Where a public sanitary sewer is not available under the provision of Section 705.040(D), the building sewer shall be connected to a private sewage disposal system complying with the provisions of this Section.
Before commencement of construction of a private sewage disposal system, the owner shall first obtain a written permit signed by the City Engineer or his/her designated representative. The application for such permit shall be made on a form furnished by the City of Kimberling City, which the applicant shall supplement by any plans, specifications and other information as are deemed necessary by the City. A permit and inspection fee of fifty dollars ($50.00) shall be paid to the City of Kimberling City at the time the application is filed.
A permit for a private sewage disposal system shall not become effective until the installation is completed to the satisfaction of the City. The designated City representative shall be allowed to inspect the work at any stage of construction. The applicant for the permit shall notify the City when the work is ready for final inspection and before any underground portions are covered. The inspection shall be made within forty-eight (48) hours of the receipt of notice.
The type, capacities, location and layout of a private sewage disposal system shall comply with all requirements of the City of Kimberling City, the Department of Public Health of the State of Missouri and the Missouri Department of Natural Resources. No permit shall be issued for any private sewage disposal system employing subsurface soil absorption facilities where the area of the lot is not large enough to accommodate an absorption field with one hundred twenty (120) feet of lateral line per bedroom and a minimum of three hundred (300) feet of lateral line for the system or where, in the opinion of the City Engineer, an adequate private sewage disposal system cannot be installed. No private or semi-public sewage disposal system shall be permitted to discharge to any natural outlet.
At such time as a public sewer becomes available within three hundred (300) feet of the property line served by a private or semi-public sewage disposal system, a direct connection to the public sewer shall be made in compliance with this Chapter within sixty (60) days after the date of official notice to do so, and the private or semi-public sewage disposal system shall be cleaned of sludge and shall be disabled as directed by the Building Inspector or Public Works Director.
In the event public sewers are not available as defined in Section 705.040(D) above, the owner shall operate and maintain the private sewage disposal facility to keep it operating effectively at all times and as acceptable to the City of Kimberling City, at no expense to the City of Kimberling City. The City reserves the right to inspect or test a private sewage disposal system at any time. In the event that such disposal system shall prove ineffective and impose a health or environmental hazard or nuisance, the owner of the system will be required to make necessary improvements within sixty (60) days of official notice from City.
No statement contained in this Section shall be construed to interfere with any additional requirements that may be imposed by the Missouri Department of Health.
[R.O. 2012 § 705.040; Ord. No. 287, 4-20-2004]
No unauthorized person shall uncover, make any connections with or opening into, use, alter or disturb any public sewer or appurtenance thereof without first obtaining a written permit from the City.
There shall be four (4) classes of service provided by the public sewer:
Normal commercial or industrial service,
Special commercial or industrial service, and
Excess BOD or suspended solid concentration service.
In all cases the owner or his/her agent shall make application on a special form furnished by the City of Kimberling City. The permit application shall be supplemented by any plans, specifications or other information considered pertinent in the judgment of the City. An administrative fee shall be paid to the City as outlined in Section 710.080.
All costs and expense incident to the installation and connection of the building sewer to the public sewer system shall be borne by the owner. The owner shall indemnify the City of Kimberling City from any loss or damage that may directly or indirectly be occasioned by the installation of the building sewer.
A separate and independent building sewer shall be provided for every building; except that, if a property is at the rear of or interior to a second property and is without public access except through the second property, and if the public sewer is available at the property line of the second property, then the property without public access shall be considered to have the public sewer available at the property line and shall be subject to the requirements of Section 705.040. All costs and expense incident to the extension of the sewer line across private property shall be borne by the owner.
Old building sewers may be used in connection with new buildings only when they are found on examination and test by the City to meet all requirements of this Section.
Methods and materials used in construction of sewers in the City of Kimberling City shall be uniform and conform as follows:
Size, slope, alignment, materials of construction of a building sewer and the methods to be used in excavating, placing of the pipe, jointing, testing and backfilling the trench shall all conform to the requirements of the Building, Plumbing and Housing Codes or other applicable rules and regulations of the City of Kimberling City.
All package sewerage grinder pumps installed in the City of Kimberling City on or after October 15, 1998, shall be semi-positive displacement type. Said grinder pumps shall only be integral, vertical rotor, motor driven, solids-handling pumps of the progressing cavity type with mechanical seals, custom designed in accordance with detailed specifications maintained by the Kimberling City Department of Public Works. Copies of grinder pump specifications will be available at City Hall.
For each connection that is permitted after February 17, 2015, in an area serviced by pressure sewer lines, the property owner shall install a grinder pump as specified by the City. A copy of specifications and approved pumps shall be available from the City. The grinder pump shall be maintained and replaced (if necessary) at the expense of the property owner.
[Ord. No. 382, 4-21-2015]
Whenever possible, the building sewer shall be placed in the building at an elevation below the basement floor. In all buildings in which any building sewer is too low to permit gravity flow to the public sewer, sanitary sewage carried by such building sewer shall be lifted by an approved means and discharged to the City sewer.
No person shall make connection of roof downspouts, interior and exterior foundation drains, areaway drains or other sources of surface runoff or ground water to a building sewer which in turn is connected directly or indirectly to any sewage disposal system.
The applicant for the building permit shall notify the City when the building sewer is ready for inspection and connection to the public sewer. The City will make all connections to the City sewer.
All excavations for building sewer installation shall be adequately guarded with barricades and lights so as to protect the public from hazard. Streets, sidewalks, parkways and other public property disturbed in the course of the work shall be restored in a manner satisfactory to the City of Kimberling City.
[R.O. 2012 § 705.045; Ord. No. 359, 3-23-2012; Ord. No. 363, 5-15-2012]
City of Kimberling City warrants that all property owners within the City limits of Kimberling City shall, subject to the provisions of this Section and other applicable ordinances of the City, be entitled to have access to the City Sanitary Sewer, provided the customer, applicant or property owner shall pay the actual cost of extension of any sewer main to the property being served, if necessary, and the actual cost of the grinder pump and associated electrical components as well as the connection into the sewer system.
Before the extension of any sewer main in the City of Kimberling City shall be made by any person, corporation, partnership or other entity, other than a City employee, application for such extension shall be made to the City Clerk.
When extending a sewer line to a single user where there is an existing main of adequate size in a street or roadway adjacent to the property or where an extension is necessary to serve a single user, the following rules and policies shall apply:
Upon proper written application, the City's Director of Public Works will make an estimate of the cost of the proposed extension, which shall include all labor, consulting engineering costs, materials, equipment rentals required, including fittings, values, value boxes, right-of-way costs, if any, and reconstruction of existing sewer mains to which the proposed extension will be connected and shall include an additional ten percent (10%) for use of small tools, appliances, transportation, storeroom and incidental expense.
The estimate in Subsection (C)(1) shall be for extending from the existing main to a point directly to the location of connection, whether being for a grinder pump or gravity connection for said property. If the existing main is not on the same side of the street as the connection location for such property, the estimated cost shall include the cost of boring under or digging through the street to install the service connection line.
The applicant shall pay to the City an amount equal to the estimated cost. Construction shall not commence until such sum has been paid. The sum so advanced by the applicant shall be adjusted to the actual cost of the work and as soon as the work is completed, the excess of the payment, if any, shall be returned to the applicant or, if actual costs exceed the estimate, the applicant will be required to pay the additional sum to the City. The additional sum and all costs of extension shall be paid before service is commenced.
When extending sewer mains into a territory or area which is unoccupied and not developed or where there are no sewer mains in the streets, roadways or rights-of-way (excluding subdivisions which fall within subdivision regulations) and the City's Director of Public Works finds that additional connections will most likely be made between the existing main and the end of the extension, the rules and policies set forth in Subsection (C) and this Subsection (D) shall apply.
Future applicants to connect to said extended line shall pay a fee to the City based upon a formula representing a reasonable pro rata charge based upon other available and prospective users of the extended line.
All sums of money collected by the City as provided by Subsection (D)(1) shall be credited to a fund designated as the "Sewer Pro Rata Fund." Money credited to the Sewer Pro Rata Fund may, at the direction of the Board of Aldermen, be used to pay all or part of the cost of the extension to the original applicant paying for such extension. All refunds hereinafter provided shall be paid from the Sewer Pro Rata Fund.
Through the completion of any extension as provided in this Subsection (D) and after the original applicant has commenced receiving service; all additional connections to applicant's sewer main extension shall be made to pay the pro rata charge as originally established to ensure payment of a refund to the original applicant not to exceed the applicant's cost of said extension. Funds remaining after the original applicant has been paid, as herein provided, shall become the property of the City.
For any extension under either Subsection (C) or (D) the following general rules and policies shall apply:
The deposits or payment of cost made by applicants as provided hereunder do not relieve any applicant from the payment of the regular service connection or tap fee as may be provided by any other ordinance in effect at the time the application is made.
The City reserves the right to further extend the main and to make connecting mains on intersecting streets or easements, and such further extensions or connections shall not entitle the original applicant to any refund by reason thereof or when other customers attach thereto as provided in Subsection (D)(3).
No interest shall be paid on any deposit made under the provisions of this Section.
Minimum pipe size for gravity sewer mains shall be eight (8) inches in diameter and a minimum of two (2) inches in diameter for pressure mains. Service connections shall be sized based on the current building codes as set forth in other ordinances. Should the City desire to install a smaller or larger pipe connection, a cost adjustment shall be established and a refund, if applicable, provided to the applicant.
An applicant shall, when requested by the City, furnish a complete plan of the proposed development, tract or lot to be served, including the location of the requested extension and a profile of the grades on roads/streets of approved easements. In the case of new developments, the City may require the developer to bring the grades of the proposed streets reasonably close to the final grade to be established before construction of the sewer main extension is commenced.
The location of all extensions shall be in established streets, alleys or approved easements with the actual location of the extension under the control of the City. Rights-of-way or easements shall be provided without cost to the City or, if payment is required, it shall be included in the cost of the extension. Rights-of-way or easements shall be granted in favor of the City.
Extensions made under the policy established by this Section shall be and remain the property of the City in consideration of its perpetual upkeep and maintenance.
Responsibility of advising the City of the proper recipient of the refunds provided herein shall rest with the applicant.
The City may, at its election, perform work provided hereunder or may allow such to be performed under contract. If the City performs the work, a complete list of all materials used, their cost and all labor cost shall be furnished to the applicant.
The City reserves the right to refuse the extension of any main if, in the judgment of the Board of Aldermen, the cost or investment would be prohibitive or the extension of the main as requested is determined to be detrimental to the City sewer system, or the present water customers.
Whenever, in the judgment of the Board of Aldermen of the City of Kimberling City, Missouri, it is found and determined to be in the best interest of the sewer system of the City of Kimberling City, Missouri, for the City to make a sewer main extension at the cost of the City and not under the policies herein provided by this Section, or where said Board determines that to follow the provisions of this Section would be an unreasonable burden on the property owners because of the length of the extension involved, said Board may waive the provisions of this Section and proceed in such other manner as the Board determines.
[R.O. 2012 § 705.050; Ord. No. 287, 4-20-2004; Ord. No. 340, 10-6-2009]
No inflow and infiltration (I&I) shall be allowed to enter into the sanitary sewer system. It shall be unlawful for any person to discharge or cause to be discharged unpolluted waters into the wastewater system. No stormwater from any yard, building or roof, footing tiles, sump pumps, swimming pool or any other natural precipitation or ground water drain of any type that can carry unpolluted waters to the sanitary sewer system shall be allowed.
No person shall discharge or cause to be discharged any stormwater, surface water, ground water, roof runoff, subsurface drainage, including interior and exterior foundation drains, uncontaminated cooling water or unpolluted industrial process waters to any sanitary sewer.
Stormwater and all other unpolluted drainage shall be discharged to such areas that are specifically designated as storm drains or to a natural outlet approved by the City. Industrial cooling water or unpolluted process waters may be discharged on approval of the City to a storm drain or natural outlet.
No person shall discharge or cause to be discharged any of the following described waters or wastes to any public sewers:
Any gasoline, benzene, naphtha, fuel oil or other flammable or explosive liquid, solids or gas.
Any waters or wastes containing toxic or poisonous solids, liquids or gases in sufficient quantity, either singly or by interaction with other wastes, to injure or interfere with any sewage treatment process, constitute a hazard to humans or animals, create a public nuisance or create any hazard in the receiving waters of the sewage treatment plant including, but not limited to cyanide in excess of two (2) mg/l as CN in the wastes as discharged to the public sewer.
Any waters or wastes having a pH lower than five and one-half (5.5) or having any other corrosive property capable of causing damage or hazard to structures, equipment and personnel.
Solid or viscous substance (grease) in quantities or of such size capable of causing obstruction to the flow in sewers or other interference with the proper operation of the sewage works such as, but not limited to, ashes, cinders, sand, mud, straw, shavings, metal, glass, rags, feathers, tar, plastics, wood, unground garbage, whole blood, paunch manure, hair and fleshings, entrails and paper dishes, cups, milk containers, etc., either whole or ground by garbage grinders.
No person shall discharge or cause to be discharged the following described substances, materials, waters or wastes if it appears likely in the opinion of the City that such wastes can harm either the sewers, sewage treatment process or equipment, have an adverse effect on the receiving stream or can otherwise endanger life, limb, public property or constitute a nuisance. In forming an opinion as to the acceptability of these wastes in relation to the flows and velocities in the sewers, materials of construction of the sewers, nature of the sewage treatment process, capacity of the sewage treatment plant and other pertinent factors, the substances prohibited are:
Any liquid or vapor having a temperature higher than one hundred fifty degrees Fahrenheit (150° F.) sixty-five degree Celsius (65° C.).
Any water or wastes containing fats, wax, grease or oils, whether emulsified or not, in excess of one hundred (100) mg/l or containing substances which may solidify or become viscous at temperatures between thirty-two degrees Fahrenheit (32° F.) and one hundred fifty degrees Fahrenheit (150° F.) sixty-five degree Celsius (65° C.).
Any garbage that has not been properly shredded.
Any waters or wastes containing strong acid iron pickling waste or concentrated plating solutions whether neutralized or not.
Any waters or wastes containing iron, chromium, copper, phosphorus, zinc and similar objectionable or toxic substances; or wastes exerting an excessive chlorine requirement.
Any waters or wastes containing high concentrations of phenols or other taste- or odor-producing substances which may pose a threat to the effectiveness of the sewage treatment plant.
Any radioactive wastes or isotopes of such half-life or concentration as may exceed limits established by the City in compliance with applicable State or Federal regulations.
Any waters or wastes having a pH in excess of nine and one-half (9.5).
Materials which exert or cause:
Unusual concentrations of inert suspended solids (such as, but not limited to, Fuller's earth, lime slurries and like residues) or of dissolved solids (such as, but not limited to, sodium chloride or sodium sulfate).
Excessive discoloration (such as, but not limited to, dye wastes and vegetable tanning solutions).
Unusual BOD, chemical oxygen demand, or chlorine requirements in such quantities as to constitute a significant load on the sewage treatment works.
Unusual volume of flow or concentration of wastes constituting "slugs" as defined herein.
Waters or wastes containing substances which are not amenable to treatment or reduction by the sewage treatment processes employed or are amenable to treatment only to such degree that the sewage treatment plant effluent cannot meet the requirements of other agencies having jurisdiction over discharge to the receiving waters.
Any waters or wastes having:
A five (5) day BOD greater than three hundred (300) parts per million by weight, or
Containing more than three hundred fifty (350) parts per million by weight or suspended solids, or
Having an average daily flow greater than two percent (2%) of the average sewage flow of the City of Kimberling City. The owner shall provide, at his/her expense, such preliminary treatment as may be necessary to:
Reduce the biochemical oxygen demand to three hundred (300) parts per million by weight, or
Reduce the suspended solids to three hundred fifty (350) parts per million by weight, or
Control the quantities and rates of discharge of such waters or wastes. Plans, specifications and any other pertinent information relating to proposed preliminary treatment facilities shall be submitted for the approval of the City and no construction of such facilities shall be commenced until said approvals are obtained in writing.
If any waters or wastes are discharged or are proposed to be discharged to the public sewers, which waters contain the substances or possess the characteristics enumerated in Subsection (D) of this Section, and which may have a deleterious effect upon the sewage works, processes, equipment or receiving waters, or which otherwise create a hazard to life to constitute a public nuisance, the City may:
Reject the wastes,
Require pretreatment to an acceptable condition for discharge to the public sewers,
Require control over the quantities and rates of discharge, and
Require payment to cover the added cost of handling and treating the wastes not covered by existing taxes or sewer charges under the provisions of Subsection (J) of this Section.
If the City permits the pretreatment or equalization of waste flows, the design and installation of the plants and equipment shall be subject to the review and approval of the City and subject to the requirements of all applicable codes, ordinances and laws.
Grease, oil and sand interceptors shall be provided when they are necessary for the proper handling of liquid wastes containing grease in excessive amount or any flammable wastes, sand or other ingredients; except that such interceptors shall not be required for private living quarters or dwelling units. All interceptors shall be of a type and capacity approved by the City and shall be located as to be readily and easily accessible for cleaning and inspection.
Where preliminary treatment or flow-equalizing facilities are provided for any waters or wastes, they shall be maintained continuously in satisfactory and effective operation by the owner at his/her expense.
The owner of any property serviced by a building sewer carrying industrial wastes shall install a suitable control manhole together with such necessary meters and other appurtenances in the building sewer to facilitate observation, sampling and measurement of the wastes. Such manhole, when required, shall be accessible and safely located and shall be constructed in accordance with plans approved by the City. The manhole shall be installed by the owner at his/her expense and shall be maintained by him/her so as to be safe and accessible at all times.
All measurements, tests and analyses of the characteristics of waters and wastes to which reference is made in this Chapter shall be determined in accordance with the latest edition of "Standard Methods for the Examination of Water and Wastewater" published by the American Public Health Association and shall be determined at the control manhole provided or upon suitable samples taken at said control manhole. In the event that no special manhole has been required, the control manhole shall be considered to be the nearest downstream manhole in the public sewer to the point at which the building sewer is connected. Sampling shall be carried out by customarily accepted methods to reflect the effect of constituents upon the sewage works and to determine the existence of hazards to life, limb and property. (The particular analyses involved will determine whether a twenty-four-hour composite of all outfalls of a premise is appropriate or whether a grab sample or samples should be taken. Normally, but not always, BOD and suspended solids analyses are obtained from twenty-four-hour composites of all outfalls whereas pHs are determined from periodic grab samples.)
No statement contained in this Section shall be construed as preventing any special agreement or arrangement between the City of Kimberling City and/or any industrial concern whereby an industrial waste of unusual strength or character may be accepted by the City of Kimberling City for treatment, subject to payment therefore by the industrial concern.
[R.O. 2012 § 705.060; Ord. No. 287, 4-20-2004]
No unauthorized person shall maliciously or willfully or negligently break, damage, destroy, uncover, deface or tamper with any structure, appurtenance or equipment which is part of the sewage works. Any person violating this provision shall be subject to immediate arrest under a charge of disorderly conduct.
[R.O. 2012 § 705.070; Ord. No. 287, 4-20-2004]
Duly authorized officials and employees of the City of Kimberling City bearing proper credentials and identification shall be permitted to enter all properties for the purposes of inspection, observation, measurement, sampling and testing of wastewater discharging into City sewers.
The officials and other duly authorized employees of the City of Kimberling City bearing proper credentials and identification shall be permitted to enter all private properties through which the City of Kimberling City holds a duly negotiated easement for the purposes of, but not limited to, inspection, observation, measurement, sampling, repair and maintenance of any portion of the sewage works lying within said easement. All entry and subsequent work, if any, on said easement shall be done in full accordance with the terms of the duly negotiated easement pertaining to the private property involved.
While performing the necessary work on private properties referred to in Subsection (A) hereof, the Superintendent or duly authorized employees of the City of Kimberling City shall observe all safety rules applicable to the premises established by the company and the company shall be held harmless for injury or death to the City of Kimberling City employees and the City of Kimberling City shall indemnify the company against loss or damage to its property by the City of Kimberling City employees and against liability claims and demands for personal injury or property damage asserted against the company and growing out of the gauging and sampling operation, except as such may be caused by negligence or failure of the company to maintain safe conditions as required in Section 705.080(H).
[R.O. 2012 § 705.080; Ord. No. 287, 4-20-2004]
Any person found to be violating any provision of this Chapter, except Section 705.090, shall be served by the City of Kimberling City with written notice stating the nature of this violation and providing a reasonable time limit for the satisfactory correction thereof. The offender shall, within the period of time stated in such notice, permanently cease all violations.
Any person who shall continue any violation beyond the time limit provided for in Subsection (A) hereof shall be guilty of an ordinance violation and on conviction thereof shall be fined in the amount not exceeding five hundred dollars ($500.00) for each violation. Each twenty-four-hour period in which any such violation shall continue shall be deemed a separate offense.
Any person violating any of the provisions of this Chapter shall become liable to the City of Kimberling City for any expense, loss or damage occasioned to the City of Kimberling City by reason of such violation.
[R.O. 2012 § 705.090; Ord. No. 287, 4-20-2004]
Any restaurant, cafeteria, business, organization or institution involved in preparation of fried food shall be required to have a grease trap. Grease traps shall conform to and be sized under the Plumbing Code in effect and shall require the approval of the City Building Inspector prior to installation.
Grease traps shall be maintained properly. Maintenance of an acceptable grease level shall be the responsibility of the establishment owner/operator. Grease removed from grease traps shall be disposed of per said code. The use of a degreaser is prohibited where its use may enter a drain that is serviced by a grease trap and/or enters into the sewage disposal system.
The City shall inspect grease traps on a basis determined by the City's designated inspector. It shall be the responsibility of the establishment owner/operator to open the grease trap for inspection by the City. The annual fee for inspection of the grease traps is seventy-five dollars ($75.00) per year per facility. The City Inspector will verify compliance. Failure to adequately maintain and clean the grease trap will result in fines as prescribed in Section 705.110.
Any establishment doing business on the date of approval of this Section shall not be required to upgrade to the standard as outlined above, as long as it can be documented that the current grease trap is operating effectively.