[Adopted 4-7-2006 by Ord. No. 2006-006]
In accordance with Chapter NR 811.08(1)(b) of the Wisconsin Administrative Code, Ledgeview Sanitary District No. 2 mandates all current or future private water systems that are connected to the municipal distribution system in more than one location and has a flow-through design are to install check valves, followed by shut off valves, at each connection to the public water system.
Also, if at any time one of the connections are severed leaving only one connection and no longer having a flow-through situation, thus creating a dead end, a flushing device must be installed and a maintenance agreement is to be filed with the District.