[HISTORY: Adopted by the Township Council of the Township of Lower Saucon as indicated in article histories. Amendments noted where applicable.]
[Adopted 9-3-2003 by Ord. No. 2003-10]
The Township hereby requires that all fire hydrants hereafter located or installed within the Township shall be equipped or installed with the following quick connect hydrant adapters and caps to the satisfaction of the Township:
Five-inch Storz permanent quick connect hydrant adapter, two stainless steel set screws mounted approximately 180° apart, watertight gasket composed of nitrile rubber, body to be composed of 6061-T6 aluminum, and manufactured to mate with a blind cap to provide a watertight seal.
Five-inch Storz permanent quick connect hydrant adapter blind cap, body to be 6061-T6 aluminum, attachment cable to be 0.125 inch vinyl-coated aircraft cable, twelve-inch long minimum, gasket to be nitrile rubber cap must be manufactured to provide a watertight seal with adapters listed above.